Oakwood Village East Health and Rehabilitation Center
|This Nursing home: 8|
|WI State Average: 5|
|U.S. Average: 4|
|WI Deficiencies Range 1–19||Updated April 18, 2013.|
How well this home met National Fire Protection Agency standards in the most recent inspection.
May 03, 2010 Fire Inspection
|Nursing Home Did Not Have:||Possible or Actual Harm||Residents Affected||Date Fixed|
|An approved automatic sprinkler system connected to the fire alarm system.||5/28/2010|
|A written emergency evacuation plan.||6/15/2010|
|Weekly inspections and monthly testing of generators.||5/27/2010|
|Corridor and hallway doors that block smoke.||5/6/2010|
|Properly maintained smoke detectors.||6/11/2010|
|Automatic sprinkler systems that have been maintained in working order.||5/14/2010|
|Exits that are accessible at all times.||5/21/2010|
|Special areas constructed so that walls can resist fire for one hour or an approved fire extinguishing system.||5/19/2010|
Note: Because of differences in calculation, all data may not match those shown on Nursing Home Compare, a website run by the federal Centers for Medicare & Medicaid Services. CMS has approved the U.S. News methodology.
Last updated April 18, 2013.