|This Nursing home: 8|
|TX State Average: 5|
|U.S. Average: 4|
|TX Deficiencies Range 1–21||Updated April 18, 2013.|
How well this home met National Fire Protection Agency standards in the most recent inspection.
November 13, 2012 Fire Inspection
|Nursing Home Did Not Have:||Possible or Actual Harm||Residents Affected||Date Fixed|
|Automatic sprinkler systems that have been maintained in working order.||12/18/2012|
|Special areas constructed so that walls can resist fire for one hour or an approved fire extinguishing system.||12/18/2012|
|Walls that prevent smoke from passing through and would resist fire for at least one hour.||12/18/2012|
|Weekly inspections and monthly testing of generators.||12/18/2012|
|Properly working alarms on sprinkler valves.||12/18/2012|
|Corridor and hallway doors that block smoke.||12/18/2012|
|Properly installed electrical wiring and equipment.||12/18/2012|
|Smoke barrier doors that can resist smoke for at least 20 minutes.||12/18/2012|
Last updated April 18, 2013.