Laurelwood Healthcare Center
|This Nursing home: 7|
|TN State Average: 3|
|U.S. Average: 4|
|TN Deficiencies Range 1–12||Updated April 18, 2013.|
How well this home met National Fire Protection Agency standards in the most recent inspection.
November 23, 2008 Fire Inspection
|Nursing Home Did Not Have:||Possible or Actual Harm||Residents Affected||Date Fixed|
|A fire alarm system that can be heard throughout the facility.||12/24/2008|
|An approved automatic sprinkler system connected to the fire alarm system.||12/24/2008|
|Corridor and hallway doors that block smoke.||12/24/2008|
|Emergency lighting that can last at least 1 1/2 hours.||12/24/2008|
|Exits that are accessible at all times.||12/24/2008|
|Properly located and lighted "exit" signs.||12/24/2008|
|Special areas constructed so that walls can resist fire for one hour or an approved fire extinguishing system.||12/24/2008|
Note: Because of differences in calculation, all data may not match those shown on Nursing Home Compare, a website run by the federal Centers for Medicare & Medicaid Services. CMS has approved the U.S. News methodology.
Last updated April 18, 2013.