|This Nursing home: 11|
|PA State Average: 5|
|U.S. Average: 4|
|PA Deficiencies Range 1–18||Updated January 21, 2014.|
How well this home met National Fire Protection Agency standards in the most recent inspection.
September 04, 2013 Fire Inspection
|Nursing Home Did Not Have:||Possible or Actual Harm||Residents Affected||Date Fixed|
|A fire alarm system that can be heard throughout the facility.||11/3/2013|
|Smoke barrier doors that can resist smoke for at least 20 minutes.||11/3/2013|
|Protected exits that allow the resident to escape the building.||11/3/2013|
|Exits that are accessible at all times.||11/3/2013|
|A two-hour-resistant firewall separation.||11/3/2013|
|An approved automatic sprinkler system connected to the fire alarm system.||11/3/2013|
|Posted "no-smoking" signs in areas where smoking is not permitted or ashtrays provided where smoking was allowed.||11/3/2013|
|Properly installed electrical wiring and equipment.||11/3/2013|
|Emergency lighting that can last at least 1 1/2 hours.||11/3/2013|
|Walls that prevent smoke from passing through and would resist fire for at least one hour.||11/3/2013|
|Automatic sprinkler systems that have been maintained in working order.||11/3/2013|
Note: Because of differences in calculation, all data may not match those shown on Nursing Home Compare, a website run by the federal Centers for Medicare & Medicaid Services. CMS has approved the U.S. News methodology.
Last updated January 21, 2014.