|This Nursing home: 9|
|PA State Average: 5|
|U.S. Average: 4|
|PA Deficiencies Range 1–18||Updated April 18, 2013.|
How well this home met National Fire Protection Agency standards in the most recent inspection.
December 28, 2011 Fire Inspection
|Nursing Home Did Not Have:||Possible or Actual Harm||Residents Affected||Date Fixed|
|Special areas constructed so that walls can resist fire for one hour or an approved fire extinguishing system.||1/27/2012|
|An approved automatic sprinkler system connected to the fire alarm system.||1/27/2012|
|Exit stairways and towers that are smoke proof.||1/27/2012|
|Exits that are accessible at all times.||1/27/2012|
|Properly constructed linen or trash chutes.||1/27/2012|
|Properly installed electrical wiring and equipment.||1/27/2012|
|Proper medical gas storage and administration areas.||1/27/2012|
|Smoke barrier doors that can resist smoke for at least 20 minutes.||1/27/2012|
|Corridors that are separated from use areas by walls constructed to limit the passage of smoke.||1/27/2012|
Note: Because of differences in calculation, all data may not match those shown on Nursing Home Compare, a website run by the federal Centers for Medicare & Medicaid Services. CMS has approved the U.S. News methodology.
Last updated April 18, 2013.