|This Nursing home: 11|
|PA State Average: 5|
|U.S. Average: 4|
|PA Deficiencies Range 1–18||Updated April 12, 2014.|
How well this home met National Fire Protection Agency standards in the most recent inspection.
September 10, 2013 Fire Inspection
|Nursing Home Did Not Have:||Possible or Actual Harm||Residents Affected||Date Fixed|
|A fire alarm system that can be heard throughout the facility.||10/15/2013|
|Protected exits that allow the resident to escape the building.||10/15/2013|
|Special areas constructed so that walls can resist fire for one hour or an approved fire extinguishing system.||10/15/2013|
|Walls that prevent smoke from passing through and would resist fire for at least one hour.||10/15/2013|
|A two-hour-resistant firewall separation.||10/15/2013|
|Automatic sprinkler systems that have been maintained in working order.||10/15/2013|
|Corridor and hallway doors that block smoke.||10/15/2013|
|Properly installed electrical wiring and equipment.||10/15/2013|
|Proper medical gas storage and administration areas.||10/15/2013|
|At least two remote exits on each floor or fire section of the building.||10/15/2013|
|Exit stairways and towers that are smoke proof.||10/15/2013|
Note: Because of differences in calculation, all data may not match those shown on Nursing Home Compare, a website run by the federal Centers for Medicare & Medicaid Services. CMS has approved the U.S. News methodology.
Last updated April 12, 2014.