|This Nursing home: 10|
|PA State Average: 5|
|U.S. Average: 4|
|PA Deficiencies Range 1–18||Updated April 12, 2014.|
How well this home met National Fire Protection Agency standards in the most recent inspection.
September 19, 2011 Fire Inspection
|Nursing Home Did Not Have:||Possible or Actual Harm||Residents Affected||Date Fixed|
|Approved construction type or materials.||11/15/2011|
|Properly installed electrical wiring and equipment.||11/15/2011|
|Automatic sprinkler systems that have been maintained in working order.||11/15/2011|
|Exits that are accessible at all times.||11/15/2011|
|Heating and ventilation systems that have been properly installed according to the manufacturer's instructions.||11/15/2011|
|Proper medical gas storage and administration areas.||11/15/2011|
|Special areas constructed so that walls can resist fire for one hour or an approved fire extinguishing system.||11/15/2011|
|A properly installed device for maintaining water pressure in the sprinkler system.||11/15/2011|
|Exit stairways and towers that are smoke proof.||11/15/2011|
|Other fire safety features required by fire safety codes.||11/15/2011|
Note: Because of differences in calculation, all data may not match those shown on Nursing Home Compare, a website run by the federal Centers for Medicare & Medicaid Services. CMS has approved the U.S. News methodology.
Last updated April 12, 2014.