Brookside Healthcare & Rehabilitation Center
|This Nursing home: 7|
|PA State Average: 5|
|U.S. Average: 4|
|PA Deficiencies Range 1–18||Updated April 18, 2013.|
How well this home met National Fire Protection Agency standards in the most recent inspection.
August 24, 2010 Fire Inspection
|Nursing Home Did Not Have:||Possible or Actual Harm||Residents Affected||Date Fixed|
|Special areas constructed so that walls can resist fire for one hour or an approved fire extinguishing system.||9/29/2010|
|Corridor and hallway doors that block smoke.||9/29/2010|
|Posted "no-smoking" signs in areas where smoking is not permitted or ashtrays provided where smoking was allowed.||9/29/2010|
|Corridors that are separated from use areas by walls constructed to limit the passage of smoke.||9/29/2010|
|Protected exits that allow the resident to escape the building.||9/29/2010|
|Exit stairways and towers that are smoke proof.||9/29/2010|
|Properly sized and located compartments to protect residents from smoke.||9/29/2010|
Last updated April 18, 2013.