Liberty Health Care Center Inc.
|This Nursing home: 10|
|OH State Average: 4|
|U.S. Average: 4|
|OH Deficiencies Range 1–28||Updated April 12, 2014.|
How well this home met National Fire Protection Agency standards in the most recent inspection.
August 10, 2011 Fire Inspection
|Nursing Home Did Not Have:||Possible or Actual Harm||Residents Affected||Date Fixed|
|An automatic smoke detection system in all hallways.||9/23/2011|
|Special areas constructed so that walls can resist fire for one hour or an approved fire extinguishing system.||9/23/2011|
|Corridors that are separated from use areas by walls constructed to limit the passage of smoke.||9/23/2011|
|Weekly inspections and monthly testing of generators.||9/23/2011|
|An approved automatic sprinkler system connected to the fire alarm system.||9/23/2011|
|Exits that are accessible at all times.||9/23/2011|
|Signs that state that exit doors are to be kept closed.||9/23/2011|
|Smoke barrier doors that can resist smoke for at least 20 minutes.||9/23/2011|
|Proper backup exit lighting.||9/23/2011|
|Emergency lighting that can last at least 1 1/2 hours.||9/23/2011|
Note: Because of differences in calculation, all data may not match those shown on Nursing Home Compare, a website run by the federal Centers for Medicare & Medicaid Services. CMS has approved the U.S. News methodology.
Last updated April 12, 2014.