Bradley Bay Health Center
|This Nursing home: 9|
|OH State Average: 4|
|U.S. Average: 4|
|OH Deficiencies Range 1–14||Updated April 18, 2013.|
How well this home met National Fire Protection Agency standards in the most recent inspection.
January 06, 2010 Fire Inspection
|Nursing Home Did Not Have:||Possible or Actual Harm||Residents Affected||Date Fixed|
|An approved back-up procedure for a faulty fire alarm system.||2/8/2010|
|Exits that are accessible at all times.||2/8/2010|
|Special areas constructed so that walls can resist fire for one hour or an approved fire extinguishing system.||2/8/2010|
|Walls that prevent smoke from passing through and would resist fire for at least one hour.||2/8/2010|
|A two-hour-resistant firewall separation.||2/8/2010|
|Properly installed electrical wiring and equipment.||2/8/2010|
|Approved construction type or materials.||2/8/2010|
|Posted "no-smoking" signs in areas where smoking is not permitted or ashtrays provided where smoking was allowed.||2/8/2010|
|Corridor and hallway doors that block smoke.||2/8/2010|
Note: Because of differences in calculation, all data may not match those shown on Nursing Home Compare, a website run by the federal Centers for Medicare & Medicaid Services. CMS has approved the U.S. News methodology.
Last updated April 18, 2013.