Westmount Health Facility
|This Nursing home: 4|
|NY State Average: 3|
|U.S. Average: 4|
|NY Deficiencies Range 1–20||Updated April 18, 2013.|
How well this home met National Fire Protection Agency standards in the most recent inspection.
January 15, 2013 Fire Inspection
|Nursing Home Did Not Have:||Possible or Actual Harm||Residents Affected||Date Fixed|
|Record of quarterly fire drills for each shift under varying conditions.||2/28/2013|
|Walls that prevent smoke from passing through and would resist fire for at least one hour.||2/28/2013|
|Automatic sprinkler systems that have been maintained in working order.||2/28/2013|
|An approved installation, maintenance and testing program for fire alarm systems.||2/28/2013|
Last updated April 18, 2013.