|This Nursing home: 7|
|MS State Average: 2|
|U.S. Average: 4|
|MS Deficiencies Range 1–7||Updated January 21, 2014.|
How well this home met National Fire Protection Agency standards in the most recent inspection.
December 14, 2012 Fire Inspection
|Nursing Home Did Not Have:||Possible or Actual Harm||Residents Affected||Date Fixed|
|Special areas constructed so that walls can resist fire for one hour or an approved fire extinguishing system.||2/21/2013|
|An approved automatic sprinkler system connected to the fire alarm system.||2/21/2013|
|Proper construction of ducts through walls designed to prevent smoke passage.||2/21/2013|
|Corridors that are separated from use areas by walls constructed to limit the passage of smoke.||2/21/2013|
|Exits that are accessible at all times.||2/21/2013|
|Corridor and hallway doors that block smoke.||2/21/2013|
|Exit doors that are held open by devices that will automatically close on the activation of a fire alarm or smoke detector.||2/21/2013|
Note: Because of differences in calculation, all data may not match those shown on Nursing Home Compare, a website run by the federal Centers for Medicare & Medicaid Services. CMS has approved the U.S. News methodology.
Last updated January 21, 2014.