Viking Manor Nursing Home
|This Nursing home: 4|
|MN State Average: 3|
|U.S. Average: 4|
|MN Deficiencies Range 1–11||Updated April 18, 2013.|
How well this home met National Fire Protection Agency standards in the most recent inspection.
May 25, 2010 Fire Inspection
|Nursing Home Did Not Have:||Possible or Actual Harm||Residents Affected||Date Fixed|
|Proper backup exit lighting.||6/18/2010|
|Special areas constructed so that walls can resist fire for one hour or an approved fire extinguishing system.||5/28/2010|
|Walls that prevent smoke from passing through and would resist fire for at least one hour.||6/18/2010|
|Automatic sprinkler systems that have been maintained in working order.||6/2/2010|
Note: Because of differences in calculation, all data may not match those shown on Nursing Home Compare, a website run by the federal Centers for Medicare & Medicaid Services. CMS has approved the U.S. News methodology.
Last updated April 18, 2013.