|This Nursing home: 12|
|MA State Average: 3|
|U.S. Average: 4|
|MA Deficiencies Range 1–12||Updated April 18, 2013.|
How well this home met National Fire Protection Agency standards in the most recent inspection.
November 30, 2011 Fire Inspection
|Nursing Home Did Not Have:||Possible or Actual Harm||Residents Affected||Date Fixed|
|An approved automatic sprinkler system connected to the fire alarm system.||1/11/2012|
|An approved installation, maintenance and testing program for fire alarm systems.||1/11/2012|
|Automatic sprinkler systems that have been maintained in working order.||1/11/2012|
|A written emergency evacuation plan.||1/11/2012|
|Exits that are free from obstructions and can be used at all times.||1/11/2012|
|Portable fire extinguishers.||1/11/2012|
|Properly installed electrical wiring and equipment.||1/11/2012|
|Properly maintained smoke detectors.||1/11/2012|
|Properly working alarms on sprinkler valves.||1/11/2012|
|Proper medical gas storage and administration areas.||1/11/2012|
|Record of quarterly fire drills for each shift under varying conditions.||1/11/2012|
|Special areas constructed so that walls can resist fire for one hour or an approved fire extinguishing system.||1/11/2012|
Note: Because of differences in calculation, all data may not match those shown on Nursing Home Compare, a website run by the federal Centers for Medicare & Medicaid Services. CMS has approved the U.S. News methodology.
Last updated April 18, 2013.