Southwood at Norwell Nursing Center
|This Nursing home: 5|
|MA State Average: 3|
|U.S. Average: 4|
|MA Deficiencies Range 1–12||Updated April 18, 2013.|
How well this home met National Fire Protection Agency standards in the most recent inspection.
January 31, 2012 Fire Inspection
|Nursing Home Did Not Have:||Possible or Actual Harm||Residents Affected||Date Fixed|
|Proper medical gas storage and administration areas.||3/19/2012|
|An approved automatic sprinkler system connected to the fire alarm system.||3/19/2012|
|Exit doors that are held open by devices that will automatically close on the activation of a fire alarm or smoke detector.||3/19/2012|
|Properly protected cooking facilities.||3/19/2012|
|Weekly inspections and monthly testing of generators.||3/19/2012|
Note: Because of differences in calculation, all data may not match those shown on Nursing Home Compare, a website run by the federal Centers for Medicare & Medicaid Services. CMS has approved the U.S. News methodology.
Last updated April 18, 2013.