Mont Marie Health Care Center
|This Nursing home: 6|
|MA State Average: 3|
|U.S. Average: 4|
|MA Deficiencies Range 1–13||Updated June 19, 2014.|
How well this home met National Fire Protection Agency standards in the most recent inspection.
July 11, 2012 Fire Inspection
|Nursing Home Did Not Have:||Possible or Actual Harm||Residents Affected||Date Fixed|
|A two-hour-resistant firewall separation.||10/15/2012|
|Doors of sufficient width and proper construction in smoke barriers.||9/15/2012|
|Proper fire barriers, ventilation and signs for the transfilling of oxygen.||9/15/2012|
|Properly constructed linen or trash chutes.||10/15/2012|
|Properly working alarms on sprinkler valves.||10/15/2012|
|Special areas constructed so that walls can resist fire for one hour or an approved fire extinguishing system.||9/15/2012|
Note: Because of differences in calculation, all data may not match those shown on Nursing Home Compare, a website run by the federal Centers for Medicare & Medicaid Services. CMS has approved the U.S. News methodology.
Last updated June 19, 2014.