|This Nursing home: 8|
|IN State Average: 4|
|U.S. Average: 4|
|IN Deficiencies Range 1–23||Updated April 18, 2013.|
How well this home met National Fire Protection Agency standards in the most recent inspection.
January 19, 2010 Fire Inspection
|Nursing Home Did Not Have:||Possible or Actual Harm||Residents Affected||Date Fixed|
|An approved automatic sprinkler system connected to the fire alarm system.||2/18/2010|
|Automatic sprinkler systems that have been maintained in working order.||2/18/2010|
|Corridors or aisles that are unobstructed and are at least 8 feet in width.||2/18/2010|
|Exits that are accessible at all times.||2/18/2010|
|Proper fire barriers, ventilation and signs for the transfilling of oxygen.||2/18/2010|
|Smoke barrier doors that can resist smoke for at least 20 minutes.||2/18/2010|
|Special areas constructed so that walls can resist fire for one hour or an approved fire extinguishing system.||2/18/2010|
|Walls that prevent smoke from passing through and would resist fire for at least one hour.||2/18/2010|
Note: Because of differences in calculation, all data may not match those shown on Nursing Home Compare, a website run by the federal Centers for Medicare & Medicaid Services. CMS has approved the U.S. News methodology.
Last updated April 18, 2013.