|This Nursing home: 15|
|IL State Average: 7|
|U.S. Average: 4|
|IL Deficiencies Range 1–29||Updated April 18, 2013.|
How well this home met National Fire Protection Agency standards in the most recent inspection.
September 06, 2012 Fire Inspection
|Nursing Home Did Not Have:||Possible or Actual Harm||Residents Affected||Date Fixed|
|Weekly inspections and monthly testing of generators.||9/25/2012|
|An automatic smoke detection system in all hallways.||10/19/2012|
|At least two compartments on every floor to protect residents from smoke.||9/28/2012|
|Automatic sprinkler systems that have been maintained in working order.||10/5/2012|
|Exit stairways and towers that are smoke proof.||9/20/2012|
|An adequate water supply for the sprinkler system.||9/12/2012|
|Corridor and hallway doors that block smoke.||10/23/2012|
|Special areas constructed so that walls can resist fire for one hour or an approved fire extinguishing system.||10/5/2012|
|Exits that are accessible at all times.||9/19/2012|
|Protected exits that allow the resident to escape the building.||9/20/2012|
|A two-hour-resistant firewall separation.||9/20/2012|
|Properly installed electrical wiring and equipment.||9/7/2012|
|Restrictions on the use of portable space heaters.||9/6/2012|
|Record of quarterly fire drills for each shift under varying conditions.||9/20/2012|
|A written emergency evacuation plan.||9/19/2012|
Note: Because of differences in calculation, all data may not match those shown on Nursing Home Compare, a website run by the federal Centers for Medicare & Medicaid Services. CMS has approved the U.S. News methodology.
Last updated April 18, 2013.