Southview Manor Nursing Center
|This Nursing home: 6|
|IL State Average: 7|
|U.S. Average: 4|
|IL Deficiencies Range 1–29||Updated April 18, 2013.|
How well this home met National Fire Protection Agency standards in the most recent inspection.
May 23, 2012 Fire Inspection
|Nursing Home Did Not Have:||Possible or Actual Harm||Residents Affected||Date Fixed|
|Automatic sprinkler systems that have been maintained in working order.||7/9/2012|
|Exit stairways and towers that are smoke proof.||8/13/2012|
|Proper stairway enclosures and vertical shafts.||7/9/2012|
|Weekly inspections and monthly testing of generators.||6/18/2012|
|Corridor and hallway doors that block smoke.||6/18/2012|
|Walls that prevent smoke from passing through and would resist fire for at least one hour.||6/18/2012|
Note: Because of differences in calculation, all data may not match those shown on Nursing Home Compare, a website run by the federal Centers for Medicare & Medicaid Services. CMS has approved the U.S. News methodology.
Last updated April 18, 2013.