Moorings Health Center
|This Nursing home: 10|
|IL State Average: 7|
|U.S. Average: 4|
|IL Deficiencies Range 1–29||Updated April 18, 2013.|
How well this home met National Fire Protection Agency standards in the most recent inspection.
April 05, 2012 Fire Inspection
|Nursing Home Did Not Have:||Possible or Actual Harm||Residents Affected||Date Fixed|
|Weekly inspections and monthly testing of generators.||4/18/2012|
|Properly maintained smoke detectors.||4/9/2012|
|Exits that are accessible at all times.||5/17/2012|
|Corridor and hallway doors that block smoke.||4/5/2012|
|Protected exits that allow the resident to escape the building.||4/5/2012|
|Special areas constructed so that walls can resist fire for one hour or an approved fire extinguishing system.||4/5/2012|
|Walls that prevent smoke from passing through and would resist fire for at least one hour.||4/5/2012|
|Proper medical gas storage and administration areas.||5/17/2012|
|Exit stairways and towers that are smoke proof.||5/17/2012|
|Properly installed hallway dispensers for alcohol-based hand rub.||4/18/2012|
Note: Because of differences in calculation, all data may not match those shown on Nursing Home Compare, a website run by the federal Centers for Medicare & Medicaid Services. CMS has approved the U.S. News methodology.
Last updated April 18, 2013.