Crawford Memorial Hospital Long-Term Care
|This Nursing home: 10|
|IL State Average: 7|
|U.S. Average: 4|
|IL Deficiencies Range 1–23||Updated April 12, 2014.|
How well this home met National Fire Protection Agency standards in the most recent inspection.
August 12, 2013 Fire Inspection
|Nursing Home Did Not Have:||Possible or Actual Harm||Residents Affected||Date Fixed|
|An approved back-up procedure for a faulty fire alarm system.||9/4/2013|
|A two-hour-resistant firewall separation.||9/25/2013|
|Automatic sprinkler systems that have been maintained in working order.||9/25/2013|
|Back-up procedures in place for a faulty automatic sprinkler system.||9/4/2013|
|Properly maintained smoke detectors.||10/31/2013|
|Properly protected cooking facilities.||9/25/2013|
|Weekly inspections and monthly testing of generators.||9/12/2013|
|Corridor and hallway doors that block smoke.||9/25/2013|
|Emergency lighting that can last at least 1 1/2 hours.||8/13/2013|
|Properly installed electrical wiring and equipment.||8/22/2013|
Note: Because of differences in calculation, all data may not match those shown on Nursing Home Compare, a website run by the federal Centers for Medicare & Medicaid Services. CMS has approved the U.S. News methodology.
Last updated April 12, 2014.