Marquis Care at Shaw Mt.
|This Nursing home: 11|
|ID State Average: 4|
|U.S. Average: 4|
|ID Deficiencies Range 1–12||Updated April 18, 2013.|
How well this home met National Fire Protection Agency standards in the most recent inspection.
March 17, 2011 Fire Inspection
|Nursing Home Did Not Have:||Possible or Actual Harm||Residents Affected||Date Fixed|
|Emergency lighting that can last at least 1 1/2 hours.||4/21/2011|
|An approved installation, maintenance and testing program for fire alarm systems.||4/21/2011|
|Weekly inspections and monthly testing of generators.||4/21/2011|
|Properly installed electrical wiring and equipment.||4/21/2011|
|Special areas constructed so that walls can resist fire for one hour or an approved fire extinguishing system.||4/21/2011|
|Walls that prevent smoke from passing through and would resist fire for at least one hour.||4/21/2011|
|An approved automatic sprinkler system connected to the fire alarm system.||4/21/2011|
|Properly installed hallway dispensers for alcohol-based hand rub.||4/21/2011|
|Smoke barrier doors that can resist smoke for at least 20 minutes.||4/21/2011|
|Corridors that are separated from use areas by walls constructed to limit the passage of smoke.||4/21/2011|
|Corridor and hallway doors that block smoke.||4/21/2011|
Note: Because of differences in calculation, all data may not match those shown on Nursing Home Compare, a website run by the federal Centers for Medicare & Medicaid Services. CMS has approved the U.S. News methodology.
Last updated April 18, 2013.