Westwood Nursing & Rehabilitation Center
|This Nursing home: 6|
|IA State Average: 4|
|U.S. Average: 4|
|IA Deficiencies Range 1–14||Updated January 21, 2014.|
How well this home met National Fire Protection Agency standards in the most recent inspection.
July 05, 2011 Fire Inspection
|Nursing Home Did Not Have:||Possible or Actual Harm||Residents Affected||Date Fixed|
|Emergency lighting that can last at least 1 1/2 hours.||7/11/2011|
|Posted "no-smoking" signs in areas where smoking is not permitted or ashtrays provided where smoking was allowed.||7/16/2011|
|Smoke barrier doors that can resist smoke for at least 20 minutes.||7/11/2011|
|Special areas constructed so that walls can resist fire for one hour or an approved fire extinguishing system.||7/11/2011|
|Properly maintained smoke detectors.||7/11/2011|
|Automatic sprinkler systems that have been maintained in working order.||7/11/2011|
Note: Because of differences in calculation, all data may not match those shown on Nursing Home Compare, a website run by the federal Centers for Medicare & Medicaid Services. CMS has approved the U.S. News methodology.
Last updated January 21, 2014.