Oaks - Athens Skilled Nursing
|This Nursing home: 8|
|GA State Average: 3|
|U.S. Average: 4|
|GA Deficiencies Range 1–13||Updated June 19, 2014.|
How well this home met National Fire Protection Agency standards in the most recent inspection.
November 29, 2012 Fire Inspection
|Nursing Home Did Not Have:||Possible or Actual Harm||Residents Affected||Date Fixed|
|An approved automatic sprinkler system connected to the fire alarm system.||1/10/2013|
|Corridor and hallway doors that block smoke.||1/10/2013|
|Emergency lighting that can last at least 1 1/2 hours.||1/10/2013|
|Walls that prevent smoke from passing through and would resist fire for at least one hour.||1/10/2013|
|Weekly inspections and monthly testing of generators.||1/10/2013|
|Restrictions on the use of flammable curtains.||1/10/2013|
|Posted "no-smoking" signs in areas where smoking is not permitted or ashtrays provided where smoking was allowed.||1/10/2013|
|Record of quarterly fire drills for each shift under varying conditions.||1/10/2013|
Note: Because of differences in calculation, all data may not match those shown on Nursing Home Compare, a website run by the federal Centers for Medicare & Medicaid Services. CMS has approved the U.S. News methodology.
Last updated June 19, 2014.