D Scott Hudgens Center for Skilled Nursing
|This Nursing home: 7|
|GA State Average: 3|
|U.S. Average: 4|
|GA Deficiencies Range 1–12||Updated April 18, 2013.|
How well this home met National Fire Protection Agency standards in the most recent inspection.
November 01, 2012 Fire Inspection
|Nursing Home Did Not Have:||Possible or Actual Harm||Residents Affected||Date Fixed|
|Walls that prevent smoke from passing through and would resist fire for at least one hour.||12/10/2012|
|Weekly inspections and monthly testing of generators.||12/10/2012|
|Emergency lighting that can last at least 1 1/2 hours.||12/10/2012|
|A fire alarm system that can be heard throughout the facility.||12/10/2012|
|Corridor and hallway doors that block smoke.||12/10/2012|
|Posted "no-smoking" signs in areas where smoking is not permitted or ashtrays provided where smoking was allowed.||12/10/2012|
|Properly located and lighted "exit" signs.||12/10/2012|
Note: Because of differences in calculation, all data may not match those shown on Nursing Home Compare, a website run by the federal Centers for Medicare & Medicaid Services. CMS has approved the U.S. News methodology.
Last updated April 18, 2013.