Avante at Mt. Dora, Inc.
|This Nursing home: 7|
|FL State Average: 3|
|U.S. Average: 4|
|FL Deficiencies Range 1–16||Updated April 12, 2014.|
How well this home met National Fire Protection Agency standards in the most recent inspection.
August 22, 2011 Fire Inspection
|Nursing Home Did Not Have:||Possible or Actual Harm||Residents Affected||Date Fixed|
|An approved installation, maintenance and testing program for fire alarm systems.||10/4/2011|
|Properly working alarms on sprinkler valves.||10/4/2011|
|Properly installed electrical wiring and equipment.||10/4/2011|
|Proper medical gas storage and administration areas.||10/4/2011|
|Special areas constructed so that walls can resist fire for one hour or an approved fire extinguishing system.||10/4/2011|
|Automatic sprinkler systems that have been maintained in working order.||10/4/2011|
|Portable fire extinguishers.||10/4/2011|
Note: Because of differences in calculation, all data may not match those shown on Nursing Home Compare, a website run by the federal Centers for Medicare & Medicaid Services. CMS has approved the U.S. News methodology.
Last updated April 12, 2014.