Kentmere Rehabilitation and Healthcare Center
|This Nursing home: 11|
|DE State Average: 3|
|U.S. Average: 4|
|DE Deficiencies Range 1–11||Updated January 21, 2014.|
How well this home met National Fire Protection Agency standards in the most recent inspection.
June 29, 2010 Fire Inspection
|Nursing Home Did Not Have:||Possible or Actual Harm||Residents Affected||Date Fixed|
|Record of quarterly fire drills for each shift under varying conditions.||8/1/2010|
|An approved back-up procedure for a faulty fire alarm system.||8/1/2010|
|Heating and ventilation systems that have been properly installed according to the manufacturer's instructions.||8/1/2010|
|Corridors or aisles that are unobstructed and are at least 8 feet in width.||8/1/2010|
|Properly maintained smoke detectors.||8/1/2010|
|Corridor and hallway doors that block smoke.||8/1/2010|
|Exits that are free from obstructions and can be used at all times.||8/1/2010|
|Properly installed electrical wiring and equipment.||8/1/2010|
|Weekly inspections and monthly testing of generators.||8/1/2010|
|Signs that state that exit doors are to be kept closed.||8/1/2010|
|Exit doors that are held open by devices that will automatically close on the activation of a fire alarm or smoke detector.||8/1/2010|
Note: Because of differences in calculation, all data may not match those shown on Nursing Home Compare, a website run by the federal Centers for Medicare & Medicaid Services. CMS has approved the U.S. News methodology.
Last updated January 21, 2014.