Lord Chamberlain Nursing & Rehabilitation Center
|This Nursing home: 5|
|CT State Average: 3|
|U.S. Average: 4|
|CT Deficiencies Range 1–10||Updated April 18, 2013.|
How well this home met National Fire Protection Agency standards in the most recent inspection.
September 22, 2011 Fire Inspection
|Nursing Home Did Not Have:||Possible or Actual Harm||Residents Affected||Date Fixed|
|Other fire safety features required by fire safety codes.||12/19/2011|
|Walls that prevent smoke from passing through and would resist fire for at least one hour.||12/19/2011|
|Corridor and hallway doors that block smoke.||12/19/2011|
|Doors of sufficient width and proper construction in smoke barriers.||12/19/2011|
|Special areas constructed so that walls can resist fire for one hour or an approved fire extinguishing system.||12/19/2011|
Note: Because of differences in calculation, all data may not match those shown on Nursing Home Compare, a website run by the federal Centers for Medicare & Medicaid Services. CMS has approved the U.S. News methodology.
Last updated April 18, 2013.